Robert, Good topic.
I found this information in my restaurant construction guidelines:
1. A minimum of 50 foot-candles shall be provided at a surface where a food employee is working with food or working with utensils or equipment such as slicers, knives, grinders, or saws where employee safety is a factor.
2.A minimum of 20 foot-cadles is required:
A. At a surface where food is provided for consumer self-service such
as buffets and salad bars or where fresh produce or packaged foods
are sold or offered for consumption
B. Inside equipment such as reach-in or under the counter refrigerators.
C. At a distance of 30 inches above the floor in areas used for hand
washing, warewashing, equipment and utensil storage, and in toilet
3. A minimum of 30 foot-candle shall be provided at a distance of thirty
inches above the floor, in walk-in refrigeration units and dry food
storage areas and in other areas and rooms during periods of cleaning.
4. Light fixtures in areas where food is prepared, open food is stored, or
utensils are cleaned shall be of shatterproof construction or shall be
protected with shatterproof sheilds.
What is a foot-candle?
How much light is given off by a candle at a distance of one foot.
Gotchya. Thanks, Andy.
|All times are GMT -5. The time now is 06:31 PM.|
Powered by vBulletin® Version 3.8.7
Copyright ©2000 - 2014, vBulletin Solutions, Inc.
vBulletin Optimisation provided by vB Optimise v2.6.0 Beta 4 (Lite) - vBulletin Mods & Addons Copyright © 2014 DragonByte Technologies Ltd.
2003 -2012 © BBQ-Brethren Inc. All rights reserved. All Content and Flaming Pig Logo are registered and protected under U.S and International Copyright and Trademarks. Content Within this Website Is Property of BBQ Brethren Inc. Reproduction or alteration is strictly prohibited.